Our building has a 208 and the requirements seem to say supports 110V and 240V and there seems to be a range, but I was curious if the 208 that the building has works with the 240 inputs. There are 2 fans with 2 plugs each for a total of 4 plugs.
I know if I have the 208s plugged in, it wont generate near the same watts as the 240; but my superiors are fine with that.
If you guys need more explanation, feel free to ask.
From the install guide:
2 AC-inputs per power supply. High-line input with power factor correction (PFC) included.
Note Power factor correction is a standard feature on all Catalyst 6500 series AC-input power supplies. PFC reduces the reactive component in the source AC current allowing higher power factors (typically 99 percent or better) and lower harmonic current components.
â¢Low-line (120 VAC nominal)-85 VAC (min) to 132 VAC (max)
â¢High-line (230 VAC nominal)-170 VAC (min) to 264 VAC (max)
You should be fine.
Please rate helpful posts.