I have a remote site with a VG248 with the following setup:
Software Version: 1.3(1)ES8.2
MWI Method: Lamp
On-Hook Voltage: 13V
Expected Voltage: 90V
We do not understand why we are only getting 13V for On-hook. The On-hook should be 90V. The result is that we never see the MWI LAMP LED turn ON for the analog phone connnected. Is this a known issue?
Thanks for any help you can give.