We are using 6500s a backbone and 3560s and 2960 as end user switches. We have PDUs and air conditioner for system room and they have Ethernet connections to 2960s. Yesterday power of air conditioners are gone for one second. Then Their web interfaces started not to work.We can ping air conditioners but web interfaces are not working. Then we reset the 2960s, air conditioner web interfaces are working now. What should the problem be? I know that if you can ping the device, everything else should work.
Resetting the device causes the device to start from the initial setup and so all the self test for the device are performed which causes the device to work fine.The reason for the device facing this issue might be some loose connections in cabling or power connections.
We are pleased to announce availability of Beta software for 16.6.3.
16.6.3 will be the second rebuild on the 16.6 release train targeted
towards Catalyst 9500/9400/9300/3850/3650 switching platforms. We are
looking for early feedback from customers befor...
Introduction Featured Speakers Luis Espejel is the Telecommunications
Manager of IENova, an Oil & Gas company. Currently he works with Cisco
IOS® and Cisco IOS XE platforms, and NX to some extent. He has also
worked as a Senior Engineer with the Routing P...
In this session you can learn more about Layer 3 multicast and the best
practices to identify possible threats and take security measures. It
provides an overview of basic multicast, the best security practices for
use of this technology, and recommendati...