I am in the follow position: 3525 IPVC gateway alarm lite is on when going from extended point of install (in data center) to PRI Port. Telco cannot loopback to the device at all. Distance from the phone room (smart jack location) to the data center is 260 feet. I tested all cabling successfully. When I take the 3525 IPVC gateway to the smart jack and plug directly into it (15ft patch cable) the alarm lite goes off and telco can loopback successfully. Is there a distance issue with the 3525 (in terms of from the smart jack to point of install in data center)? I do not want to leave the hardware in the phone room as we are in a single story multi-tennant building. Has anyone had this issue? Any ideas or help is appreciated!
I don't have experience with that particular box - but as long as it supports PRI signalling (i.e., B8ZS/ESF) and can provide a line build out to overcome the distance issues here, it will probably do the job.
The short answer is that you don't.... That isn't entirely true while at
the same time it kind of is, but for the most part you don't configure
the softkeys. You enable or disable them via TCL. Here is the long
answer. Be sure to read the whole thing or e...
Topology: IP Phone > Switches > Microsoft NPS setup to forward 802.1x
proxy to > ISE 2.1 patch 3 Authentication: EAP-TLS using Cisco MIC SANs
Phone Models 802.1X support? 802.1x flavor Addtl Comment EAP-MD5 EAP-TLS
Cisco 3905 Y Y N Cisco 6911 Y Y N Cisco ...
This document describe how DST changes and how time changes are
implemented in DST. Daylight Saving Time (DST) is the practice of
setting the clocks forward 1 hour from standard time during the summer
months, and back again in the fall, in order to make b...