Problem with VG248 and Fire Alarm Company. Call is made by Fire Panel. Once the Call is established it send a fire code to Provider. The call goes through but the call drops when codes are sent. Alarm company is saying that the line must be a traditional pots line. Any help would be appreciated.
In my experience with the VG248 I would say that the lines should be able to do anything that a POTS line is capable of. When the call is established you said that codes are sent, can you tell us if this means a sequence of DTMF tones or something else? Are there any Hookflashes involved? Perhaps it is something to do with the "Call Control Mode".Check out this link to see if it helps:
Thanks for the response, in my case the Alarm Company monitors residents in aged care facility.
There are 3x VG248 for the resident phones, the phones have emergency capability that send DTMF Codes to the alarm monitoring company, the alarm company uses these DTMF codes to identify the room numbers, alarm type and Person who triggered the alarm.
Replacing it with traditional pots will be expensive solution. Will VG224 work?
I heard from a friend the issue is related to the DTMF sample size used by VG248, default 100ms.
Could it be related to the DTMF sample size??? Thanks for your help.
From memory we ended up fixing the issue, In our case the issue was the duration of the DTMF tones. The DTMF tones sent by the Cisco equipment to the monitoring company was fast, monitoring company was not able to catch all the tones. Adjusting the duration on the Service parameter resolved the issue. The ISDN Gateway was H.323. What is your voice gateways protocol , MGCP or H323?
The short answer is that you don't.... That isn't entirely true while at
the same time it kind of is, but for the most part you don't configure
the softkeys. You enable or disable them via TCL. Here is the long
answer. Be sure to read the whole thing or e...
Topology: IP Phone > Switches > Microsoft NPS setup to forward 802.1x
proxy to > ISE 2.1 patch 3 Authentication: EAP-TLS using Cisco MIC SANs
Phone Models 802.1X support? 802.1x flavor Addtl Comment EAP-MD5 EAP-TLS
Cisco 3905 Y Y N Cisco 6911 Y Y N Cisco ...
This document describe how DST changes and how time changes are
implemented in DST. Daylight Saving Time (DST) is the practice of
setting the clocks forward 1 hour from standard time during the summer
months, and back again in the fall, in order to make b...